- Buyer EQUI
- Brand Carrier
Must be used where low evaporator temperatures or nuisance tripping of low-pressure switch may be encountered. Control should be wired in parallel with low-pressure switch. This allows a delay of approximately 3 minutes before low-pressure switch becomes a part of control circuit.
Required in low ambient applications where MotorMaster is used (not required on heat pumps).